All biopotential recordings can suffer from 50/60Hz interference. The largest contributors to problems are mains ground wiring and florescent fixtures.
For lighting we would recommend incandescent fixtures, perhaps low voltage (non-switching) halogen. For a very low power alternative, LED lighting would be an excellent choice, so long as AC/DC conversion elements are not introduced into the environment of the room. Its best to keep all switching elements associated with lighting out of the room. Fluorescents are not recommended due to high frequency EMI.
The electrical mains grounding should be as good as possible. This would imply using low gauge wiring (beefy wire) on all outlet ground connections and run each outlet solidly to mains ground at the sub-distribution panel.
It would be best not to daisy chain the electrical outlets in the room. It would be best if each outlet had a line which ran back directly to the sub panel breaker, In this manner the sub-panel would act as the common distribution point for all power issued to the room.
This electrical design is very helpful when the room is used in practice. For example, if some equipment is brought into the room which generates mains conducted EMI, this potential EMI will be very well isolated from other room outlets.
Workflow—A Great Tool for Every Researcher! Automate AcqKnowledge with New Workflow Tool New automation tool significantly saves time and improves consistency with standardized procedures Workflow’s drag-and-drop interface allows you to automate and repeat the signal-conditioning and processing steps your protocol requires in an easy-to-use process without programming or scripting knowledge. Batch process multiple files with confidence […]
The mind and body work together in many ways and psychophysiology research provides insight to these connections. BIOPAC has a variety of systems to power your emotion, arousal, stress, cognitive assessment, group interaction, startle, and other psychophysiology research. Here are some recent studies that have used BIOPAC systems for psychophysiological research… Skin conductance, facial EMG, […]
For immediate release: January 4, 2023 Amiens, France and GOLETA, California, USA Seenel Imaging SAS and BIOPAC Systems, Inc. have formed a long-term global partnership to distribute MedelOpt®, Seenel Imaging’s groundbreaking wearable neuroimaging device for the neuroscience research market. Seenel Imaging, based in France, continues its international expansion by partnering with BIOPAC Systems, […]